PORTABLE FIRE EXTINGUISHERS AS2444
Portable Fire Extinguishers need to be tagged & tested every six (6) months. All fire extinguishers need to be refilled and pressure tested every five (5) years. AS2444-requires extinguishers to be located approximately every 20m. All extinguishers need to be installed with its correct bracket, signage, tags and seals.
FIRE HOSE REELS AS2441
Fire Hose Reels need to be tested every six (6) months. Fire Hose Reels are 36m in length and can cover a diameter of approximately 40m from the point of installment. We can test your fire hose reels & replace if leaking or faulty.
Fire Hydrants are tagged & tested every 6 months. They are used by the NSWFB in an emergency situation. We check that they are clean, accessible & have the correct NSW storz thread along with water pressure for when the NSWFB need to use them. We tag and test each hydrant. Hydrants pump set (electric & diesel) are quoted on a per job basis.
Information by fire protection Albury